Payment & Shipping Terms:
|Cooling Power:||5500w||Benefits:||Quick Installation|
|Model:||Industrial Cooling||Suitable Usage:||Supplying Direct Cold Air|
|Feature:||Rugged Designs For Harsh Environments||Refrigerant Gas:||R22 / R410A|
This 5.5kw spot air cooler is a Portable Refrigerated Air Conditioner known as a Spot Cooler and they are available for both hire, rental and sale. Spot Cooler 5.5kW features temperature control, a mounted condensate tank, a durable design and are reliable and slightly smaller than other Spot Coolers. Spot cooler provides direct cold air to your designated area and are commonly used in offices, server rooms, workshops, hospitals, aged care or wherever direct cold air is required.
1. Full intelligent control, humidity adjustable.
2. Embedded portable cover plate, easy to repair and clean, can be artificially added water
3. Dry and wet separation design, independent electronic control system, operation is more secure and reliable.
4. Humidity control, timing control, switch control can be chosen in a variety of ways.
5. The machine adopts the anti-burn and anti-corrosion design, which is very sage and durable.
Cooling Setup: Bring timely & quickly cooling to building occupants when the central HVAC system is turned off.
Heating Setup: Portable heat pump combines both cooling and heating capabilities in a single, self-contained unit, it offers significantly higher performance, along with the usual high levels of Weixuan quality and reliability.
Dehumidifying Setup: Effective water-damage restoration begins with Weixuan . Dry rooms out quickly to reduce the formation of mold and mildew, and keep them from spreading further. A Weixuan portable unit ensures substantially faster recovery than with fans or dehumidifiers, reducing restoration costs.
|Current Consumption||8.4amps at 220 Volts|
|Airflow Evaporator||780m3 / Hour|
More details of spot cooler rental
There are two fi lters in the unit. The evaporator fi lter is located at the front of the unit. The condenser fi lter is located at the side of the unit.
1. loosen up 2 bolts on the front fi lter guard.
2. If the fi lter is heavily covered with dust and dirt, warm water and mild soap or neutral detergent may be used to wash the fi lter. Do not use any other chemicals to clean fi lter, as they will likely damage the fi lter.
3. Replace the clean fi lter and close the fi lter guard.
4. To clean the condenser fi lter, lift up on the side fi lter from the middle bar slightly and then angle the fi lter outwards from the bottom and remove.
5.Use the same cleaning procedure as above (3 – 5).
Contact Person: wang